This page documents the UL (Underwriters Laboratories) conditions of acceptability for the Accu-CT® family of current transformers, ACTL-0750 and ACTL-1250 series. The conditions of acceptability are not generally needed when using the Accu-CT with a WattNode meter, but if you are using it in other applications or seeking approval to use it with other devices, these may be needed.
Energy-monitoring Current Transformers, Series ACTL-0750 and ACTL-1250 series may be followed by numbers followed by dash, may be followed by characters.
Energy-monitoring Current Transformers Certified for Canada, Series ACTL-0750 and ACTL-1250 series may be followed by numbers followed by dash, may be followed by characters.
These devices are single-phase open type air cooled encapsulated current transformers. They may be provided with a burden resistor that enables AC voltage secondary output.
They are suitable for use in 55°C ambient in accordance with the requirements of IEEE Standard C57.13-1993 and CAN/CSA 60044-1.
CONDITIONS OF ACCEPTABILITY
- The transformers shall be installed within equipment that will provide an acceptable enclosure.
- The suitability of the lead wires shall be determined in the end use product.
- These transformers have not been tested for accuracy, impulse and mechanical tests, only temperature and dielectric voltage-withstand tests were performed.
- The acceptability of the mounting means for these transformers shall be judged in the end use.